Executive Summary of the Interim Report
Investigation Committee on the Accidents at Fukushima Nuclear Power Stations of Tokyo Electric Power Company
December 26, 2011
Table of contents
2. Outline of the Accidents
3. Issues of responses by government organizations to the Accidents
(1) Issues of the local nuclear emergency response headquarters
(2) Issues of the nuclear emergency response headquarters
(3) Remaining issues
4. Issues of responses to the Accidents at the Fukushima Dai-ichi NPS
(1) Misjudgment of operational situation of IC at Unit 1
(2) Poor handling of alternative water injections at Unit 3
(3) Relation with explosions in the Units 1 and 3 reactor buildings
5. Issues relating to the measures for preventing the expansion of damage
(1) Issues relating to the initial radiation monitoring
(2) Issues relating to the utilization of SPEEDI
(3) Issues relating to the decision-making of evacuation of residents and confusion at localities
(4) Issues relating to providing information to the nation and international society
(5) Review of other measures for preventing the expansion of damage
(1) Inappropriate measures against tsunami and severe accident
(2) Issues relating to measures by TEPCO against natural disasters
7. Why were the measures against tsunami and severe accident insufficient?
8. Recommendations on the new nuclear safety regulatory body
9. Preliminary conclusions
The Investigation Committee on the Accidents at the Fukushima Nuclear Power Stations (“the Investigation Committee”) of Tokyo Electric Power Company (TEPCO)
was established by the Cabinet decision on May 24, 2011.
Its objectives are: to conduct investigation and evaluation for finding out the causes of Accidents at the Fukushima Dai-ichi Nuclear Power Station (Fukushima Dai-ichi NPS) and Fukushima Dai-ni Nuclear Power Station (Fukushima Dai-ni NPS) of TEPCO as well as the causes of accident damage; and to make policy recommendations for limiting the expansion of damage and preventing reoccurrence of similar accident.
The Investigation Committee has conducted its investigation and evaluation since its first meeting on June 7, 2011. Its activities included: site visits to the Fukushima
Dai-ichi and Dai-ni NPSs, as well as to other facilities; hearing of heads of local governments around the Fukushima Dai-ichi NPS; and hearing of people concerned
through interviews mainly by the Secretariat. As of December 16, 2011, the number of interviewees reached 456.
The investigation and evaluation by the Investigation Committee are still ongoing and the Interim Report does not cover every item that the Committee aims at
investigating and evaluating. Fact-finding of even some of those items discussed in the Interim Report are not yet completed.
The Investigation Committee continues to conduct its investigation and evaluation and will issue its Final Report in the summer of 2012.
This brief executive summary covers mainly considerations and evaluation of the issues in Chapter VII of the Interim Report, with brief reference to Chapters I to VI.
The Investigation Committee recommendations are printed in bold.
[toggle_simple title=”Related articles” width=”600″]
- WMO support to nuclear emergency from the Fukushima Daiichi NPP accident (enformable.com)
- Japan’s response to crisis at Fukushima Dai-ichi nuclear power plant after … – NEWS.com.au (enformable.com)
- TEPCO denies reports to decommission Fukushima Daiichi Units 5 and 6 (enformable.com)
- November 2011 – INPO – Special Report on Fukushima Daiichi Nuclear Accident (enformable.com)
- TEPCO to release interim report on Fukushima nuclear accident in November (enformable.com)
- October 2011 – Review of Accident at Fukushima Daiichi – Proposed Countermeasures (enformable.com)
- Cesium levels around Fukushima Daiichi exceed 50,000 bq/kg in many areas (enformable.com)
- March 14th, 2011 – Looks like RCIC at Fukushima Daiichi Unit 2 has failed. (enformable.com)
- Fukushima – Compensation of Nuclear Damage after Great Earthquake in Japan (enformable.com)
- Evaluation Status of Reactor Core Damage at Fukushima Daiichi (enformable.com)
- Airborne Radiation Dose Measured at 1st floor of Fukushima Daiichi Unit 3 (enformable.com)
- Is the main stream media able to report on a nuclear accident? (enformable.com)
- November 17th, 2011 – TEPCO’s Roadmap to Restoration at Fukushima Daiichi (enformable.com)
- The Fukushima Daiichi Incident and Earthquake Presentation (enformable.com)
- April 2011 – Risk versus Concern – Public Health Messaging of the Fukushima Daiichi Nuclear Power Plant Incident (enformable.com)
- Japan Headlines – Nuclear safety inadequate – TEPCO blames Tsunami (enformable.com)
- TEPCO Tsunami Assessment for Nuclear Power Plants in Japan (enformable.com)
- Restart of Japanese Nuclear Plants Should Be Postponed Until Crisis Over – At Least (enformable.com)